Our best-selling High-Flow system just got better! Improved Dry Membrane design now with 20% increase in flow rate. Up to 1,200+ GPD!
Part Number: HL 31023
MSRP: $ 924.95
A: Reverse osmosis membranes like water to run through them often in order to perform properly. Running water for once a day for a short period of time is ideal, but even once a week is sufficient. If you are not going to use your reverse osmosis system for 3–4 weeks or longer, there are storage procedures you should follow to maintain optimum system performance. Take the membrane(s) out of the system and place in a plastic bag and put them in the refrigerator. A white plastic kitchen bag with a knot tied at the top works well. Take the carbon filter (and in some systems such as the Stealth-100/200™ the sediment filter as well) out of the housing and let it (them) dry out. Leave the housings and the caps on the system unscrewed to let them dry out. The purpose of this is to not trap wet filters and moisture in the system so that bacteria will not grow. As an extra measure of precaution, sterilizing using a light bleach or hydrogen peroxide solution to clean the housings, tubing and fittings is a good idea before using the system again.
A: The Evolution is not really designed to be an under the sink drinking water system. The reason for this is because the large membranes in that system perform what is called “tds creep.” This means upon system start up the ppm’s will come out higher for a minute or two and then go back down to the 94/95% ppm rejection that is standard. This happens because there is untreated water in the membranes/housings from the last time you ran the system and then shut it off. When filling a 50 or 100 gallon reservoir this really is insignificant as it evens out with the rest of the purified water. One option for using the Evolution for drinking water is to use it to fill 5 gallon jugs and put them on a water dispenser (like the ceramic ones). We also have post-remineralization filters that polish the flavor that can be perceived as flat to some people. The remin filter adds soluble calcium and makes the water more alkaline and sweetens the flavor a bit. We also have a system that is specifically designed as an under the sink drinking water system. This is called the ecospring™. There is also the option to turn a Stealth-RO100™ or -RO200™ into a drinking water system by purchasing the Stealth drinking water upgrade kit.
A: RO product water can have a lower pH than the feed water. It depends on the level of dissolved CO2 in the feed water. A lowering of pH can occur because the existing CO2 in the water, being a gas, passes through the membrane but the alkaline constituents, primarily HCO3 (bicarbonate), are removed as part of the reject water. In the feed water the HCO3 neutralizes the acid-causing CO2. In the product water, with HCO3, greatly reduced, the CO2 is free to combine with the H2O to form carbonic acid: CO2 + H2O > H2CO.
Another reason to question the pH reading is that for any water sample which is very low in TDS it is very hard to obtain an accurate pH value. The worst case of this accuracy problem occurs with de-ionized water but some low TDS RO water will react the same. The sample is so low in minerals that there is no buffer. The slightest absorption or loss of CO2 shifts the pH substantially. The water’s tendency to pick up additional CO2 from the ambient air, even if the test is done on site, can produce a very low false pH.
In reality, measuring the pH of RO water is difficult and not accurate due to lack of any pH buffering the RO water. If the feed water has a lot of dissolved CO2 then pH can drop a few points. But, in the case of a drinking water RO system, a post re-mineralization filter will help neutralize the final product water’s pH level. In the case of RO water for horticultural purposes, once you mix a calcium/magnesium supplement into the RO water and then add your nutrients and additives, the final pH can be adjusted and your feed formula should be pH stable.
A: Here are the most common challenges when filtering well water:
A: There are different methods of treating iron depending on how much iron is present in the source water. The easiest way to know how much iron you have is to get your water tested from NTL.
A: If your carbon or sediment filter apprears to be red, maroon, orange or brown in color you have iron in your water. You may also notice that your sinks and or toilets also have this discloration. See an example image below of a system that was used to fiter water with excessive iron levels.
A: This is common, there is generally a significant pH spike from the GAC (granular activated carbon) that is mitigated relatively quickly after start up. For some systems, it can take days or even weeks to run enough rinse water to get the pH back to normal. Since it is temporary, it is generally not a significant issue. For more information contact HydroLogic.